Dirty Water Pump [WQ(D)Y10T]
Dirty water pump [WQ(D)Y10T]
Dirty water pump [WQ(D)Y10T]
1.Product Introduction of the Dirty water pump [WQ(D)Y10T]
Successed new generation of high delivery cutting pump,as overturned the disadvantage of traditional sewage pump, cutting pump,integrated the advantage of clean water pump, sewage pump, cutting pump and oil-immersed motor, adopted the most advanced cutting structure, with large flow, high delivery, strong cleaning ability, well deserved the most ideal & practical cutting pump and the best-selling products beyond the user’s expectation.
1.Application Voltage 150~230V (Start by 80V / 380V
2.Sewage/Clean water, the temperature can not exceed 40℃
3.PH of water : 4 ~ 10
4.Frequency : 50Hz, Voltage : single-phase 220V,
5.Range of voltage fluctuation: ± 10% of the rating
6.Immersion depth can not more than 5m and can not lower than the height of pump.
Widely used in construction sites, mines and factories,septic tanks,municipal environmental protection and so on,can be used for sewage with long fiber, plastic bag,cloth, rope and leaves.more can be used in clear water irrigation and drainage.
2.Product Parameter（Specification）of the Dirty water pump [WQ(D)Y10T]
3.Product Feature And Application of the Dirty water pump [WQ(D)Y10T]
4.Production Details of the Dirty water pump [WQ(D)Y10T]
5.Product Qualification of the Dirty water pump [WQ(D)Y10T]
6.Installation,use and points for attention of the Dirty water pump [WQ(D)Y10T]
1.At the beginning of installation, fasten pump well first, then install electroshock pro-tection apparatus at one end of sourse conveyer wire; pay attention to earth signal for every pump,and put to earth reliably; the plug attached to pump must insert an earthed socket. In case of electrical leakage, earthing wire may supply, leakage current loop to avoid electroshock accident. Measure insulation resistance of motor winding,and the result should be bigger the than 50 megohm.Othermise,should examine the reason. It can be used again only after moisture is eliminated.
2.Switch on pump and let it run freely for several seconds, and check the situations of start,running and rotation direction directrion(for three-phase pump, if find wrong rotation direction,shold exchange the link of any two wires of power exit). Then suitch it on, if find no or very little water drawn out, it means the rotation direction is wrong, you have to exchang wiring.
Q: How to proceed an order for water pump?
A: Firstly let us know your requirements ( product details ).
Secondly We quote according to your requirements or our suggestions.
After then we arrange the production after receive your deposit.
Q: What's your product MOQ of it?
A: Our company is pleasure accept all items 1pcs order.
Q: Can I get some samples?
A: We are pleased to offer you samples.
Q: Is it OK to print my logo on pump?
A: Sure. Please inform us formally before our production and confirm the design firstly .