Submersible sewage pump [WQ(D)Y5T]
1. Product Introduction
Successed new generation of high delivery cutting pump,as overturned the disadvantage of traditional sewage pump, cutting pump,integrated the advantage of clean water pump, sewage pump, cutting pump and oil-immersed motor, adopted the most advanced cutting structure, with large flow, high delivery, strong cleaning ability, well deserved the most ideal & practical cutting pump and the best-selling products beyond the user’s expectation.
1.Application Voltage 150~230V (Start by 80V / 380V
2.Sewage/Clean water, the temperature can not exceed 40℃
3.PH of water : 4 ~ 10
4.Frequency : 50Hz, Voltage : single-phase 220V,
5.Range of voltage fluctuation: ± 10% of the rating
6.Immersion depth can not more than 5m and can not lower than the height of pump.
Widely used in construction sites, mines and factories,septic tanks,municipal environmental protection and so on,can be used for sewage with long fiber, plastic bag,cloth, rope and leaves.more can be used in clear water irrigation and drainage.
3.Product Feature And Application
6.Maintenance of the Submersible sewage pump
1 Determine the correct direction of rotation of the motor
The direction of rotation of the motor should be clarified. Many types of submersible sewage pumps can now produce water when they are rotating and rotating. However, when the water is turned, the amount of water is small and the current is large. If the rotation time is long, the motor windings will be damaged.
2 Prevent the power supply voltage from starting abnormally
Because the low-voltage power supply line is relatively long, the end voltage of the line is too low is a common occurrence. When the phase voltage is lower than 198 volts and the line voltage is lower than 342 volts, the motor speed of the submersible sewage pump is reduced. When the 70% of the additional speed is not reached, the centrifugal switch will be turned off, and the starting winding will be energized for a long time to heat up and even burn. Bad windings and capacitors. Conversely, a voltage that is too high causes the motor to overheat and burn out the windings. Therefore, in the operation of the submersible sewage pump, the operator must investigate the value of the power supply voltage at any time. If it is less than 10% of the extra voltage and higher than 10% of the extra voltage, the motor should be stopped, the cause should be found and the fault should be eliminated.
3 Insulation resistance requirements of cable line devices and submersible sewage pumps
When installing the submersible sewage pump, the cable should be overhead and the power cord should not be too long. Do not force the cable when the submersible sewage pump is launched or raised to prevent the power cord from cracking. Do not sink into the mud when the submersible pump is working, otherwise it will cause the motor to dissipate heat and burn the motor windings. When the device is installed, the insulation resistance of the motor should not be less than 0.5 megohm.
Q: What's your product MOQ of it?
A: Our company is pleasure accept all items 1pcs order.
Q: How do you ship the goods and how long does it take to arrive?
A: We usually ship by DHL, UPS, FedEx or TNT. It usually takes 3-5 days to arrive. Airline and sea shipping also optional.
Q: Are you a factory?
A: Yes. We are a factory with more than 10 years manufacturing experience.